The purpose of this Guidance Note is to inform asset managers, property managers and facilities managers on the arrangements involved in undertaking a water audit.
Water audits are a form of assessment which help to establish the way in which water is used in a property, to determine whether water management arrangements are being followed and are effective, and to identify opportunities to improve water management and performance.
Alongside the general considerations involved in auditing other utilities, for example energy, there are a number of specific challenges in assessing water consumption:
As a result, water meters can go through extensive periods where they remain unread, resulting in estimated consumption and cost, and presenting challenges for the effective management of water management activities.
A water audit can help respond to this by reviewing the availability and quality of water data and associated water management arrangements.
Note: Testing of man-made water systems within properties to control potential outbreaks of legionella in the workplace, as set out by the Health and Safety Executive’s Approved Code of Practice ACOP L8, is out of the scope of this Guidance Note.
Prolonged periods of estimated invoicing can have significant impacts on both a business’s financial management and resource deployment.
The pre-requisite inventory consolidation and verification for a water audit will help mitigate these impacts through:
Water audits will help to define the opportunity to reduce consumption, which in turn will:
The table below summarises the key activities associated with water audits, and highlights where asset managers, property managers and facilities managers are likely to have a responsibility or specific interest.
Step 1: (Water Audit) Establish audit oversight and scope
Step 2: (Water Audit) Secure a competent water assessor
Step 3: (Water Audit) Review water consumption
Step 4: (Water Audit) Review water management arrangements
Step 5: (Water Audit) Identify improvement opportunities
Step 6: (Water Audit) Review and continue to improve
Step 1: (Water meter inventory & consumption baseline) Obtain the water bills and meter readings
Step 2: (Water meter inventory & consumption baseline) Locate the water meter
Step 3: (Water meter inventory & consumption baseline) Check the meter serial number matches the water bill
Step 4: (Water meter inventory & consumption baseline) Read and record actual readings from the water meter(s)
Step 5: (Water meter inventory & consumption baseline) Verify the water bill readings against the actual meter readings
Step 6: (Water meter inventory & consumption baseline) Calculate a property’s water consumptions
Undertaking a water audit
A water audit is usually established at the property level, although it is possible to combine an audit across multiple sites, and a program of water audits is often undertaken at a portfolio level.
The decision to implement a water audit is usually taken by an asset manager. However, a property manager will often be responsible for coordinating the audit process, with information and support provided by a facilities manager. The audit outcomes will be of interest to all stakeholders.
The process of undertaking a water audit should take place within a wider framework for the governance of audit and assurance activities, and should include the following steps:
It is important that a forum, committee or body is established to provide oversight of the audit process, to validate outcomes, and to check that recommended actions are allocated appropriately.
The scope of a water audit should be agreed by the oversight body before it is undertaken.
Determining the audit scope should involve consideration of a number of issues:
Property managers should triage meters within an asset, or assets within a portfolio, in preparation for intervention.
Rateable value supplies should generally be excluded from the scope of a water audit, as these supplies are typically low consuming. This is also the case for low consuming metered supplies, as the cost of interventions will likely outweigh the benefits.
While there are no mandated qualifications or accreditations to undertake a water audit, the individual undertaking the assessment should have knowledge and experience appropriate to the audit’s scope.
As a minimum, a water auditor should have experience in relation to energy management, the property and equipment type involved, and the processes and arrangements involved in audit and assurance activities.
Free guidance is available online on how to undertake a water audit. However, if water related infrastructure, plant and supply optimization are included in the scope, specialist industry equipment and knowledge will be necessary.
Considerations when contracting a third party to undertake a water audit:
The review of a property’s water consumption profile is a central element of a water audit. The energy consumption profile should be compared against historical trends, with the intention of identifying the areas of greatest consumption and anomalies in expected consumption.
Performance against historical water targets should be reviewed to determine the extent that progress towards intended improvements is on track.
Alongside this, a water audit should consider management arrangements, such as metering arrangements, processes review water consumption and arrangements to check that recommended actions from previous water audits are being deployed. There should be evidence that such arrangements are in place and are being implemented.
A key component of a water audit is to identify opportunities to improve water efficiency. This is partly informed through the analysis of a property’s water consumption profile, and is complemented by observation of equipment, operational practices and billing arrangements.
Consideration should be given to the following:
The outcomes from a water audit, including recommended improvement actions, should be documented and reviewed by the oversight body. An action plan should set out improvement opportunities alongside timeframes and responsibilities, and should inform the development of water targets.
Ongoing water consumption, progress against targets and the implementation of action plans should be periodically reviewed by the oversight body, or an appropriate forum with responsibility for a property’s water or environmental management activities.
Creating a water meter inventory and consumption baseline
Establishing a water meter inventory for a property, and the consumption through those meters, enables a consumption baseline to be established, against which improvement targets can be set.
The following steps should be followed in order to establish a building’s baseline water usage:
Rateable value supplies will not have meter readings but estimated annual consumption figures.
Some metered supplies will include both a main and a bypass meter, with the latter recording water at low flow rates. You will need consumption from both of these meters.
It is usually located by the boundary of the property, often near a road. Your water retailer will be able to advise of the location details as held in CMOS, should identification prove challenging.
The serial number can be found on the face of the meter, or etched in the metal meter casing.
If the serial number does not match that on the bill, or you are still unable to identify the meter, ask your water retailer to raise a C/01 form, which compels the water wholesaler to undertake a meter verification visit and will help to identify the meter, or update the meter details should they differ from the invoices.
It is important to take regular recording of meter readings to enable the identification of trends in water consumption.
In most buildings, meters will need to be manually read.
How to manually read a water meter:
Automatic Meter Reading (AMR) equipment can be added to meters. AMRs take a reading, log the data and communicate it to utility companies and/or property managers.
There are also prism-lensed cameras that can be affixed to meters set to take photos on a period basis and transfer the data electronically to a central database.
It is usual for only large users of water, who are predominantly in the manufacturing sector, to receive regular bills based on meter readings. The water bills for most buildings will be based on estimated readings.
Submitting the readings you take to the supplier will ensure invoice consumption data tallies with the readings you take on site, and provide a host of ancillary benefits such as better budget management and minimising supplier queries.
As a minimum, a property’s water consumptions should be calculated annually. Ideally, more frequent usage levels should be calculated, such as monthly or weekly.
Sub-metering can provide detailed consumption data but is typically only installed in buildings with large water consuming items of equipment or areas, for example, swimming pool. However, the cost of installing sub-metering is now reducing increasing the opportunities for installation.
The following Guidance Notes contain related information:
Waterwise - a UK-based NGO supporting supply and demand side activities to reduce water consumption, including the ‘Water Mark’ certificate to organisations with a water management plan.
Alliance for Water Efficiency - a US-based NGO supporting demand-side water efficiency activities.